We are using (2) JACEs on a building network and are having issues with the Siemens System 600 / Apogee Driver skipping 5/22 points on each of the (7) “Cabinets”. Upon activating the Debug Mode and monitoring the Application Director the output displayed that 5 of 22 points are being skipped and no Point Log Report is being initiated for these 5 points on each of the 7 Cabinets. This seems unusual since the points were originally discovered by the driver but since have stopped updating which was confirmed by monitoring the Application Director output.
We have tried increasing the interchar delay to 50ms, increasing the timeout from 5,000ms incrementally up to 60,000ms, rebooted the JACE(s), forcing the update action on the points and also tested using batch polling but without success. Any way to get these points to update since they were originally discovered by the driver and just stopped updating?